Honeywell Ignition Control Board
Universal Intermittent Pilot Ignition Module
Universal intermittent pilot ignition module replaces multiple field installed intermittent pilot modules supplied by Honeywell, Robertshaw, Johnson, and UTEC (HSC). Uses existing intermittent pilot burner. Includes cross reference, instructions, and accessories for easy replacement.
¡¤ Replaces over 400 White-Rogers, Robertshaw and Honeywell intermittent pilot ignition modules
¡¤ Provides ignition sequencing, flame monitoring and safety shutoff for intermittent pilot warm air furnaces and heating appliances
¡¤ Provides 100 percent pilot gas shutoff if pilot fails to light; after 5-minute delay, trial for ignition is repeated. Ignition trial/delay sequence is repeated until the appliance lights or call for heat is removed.
¡¤ For use with Natural or LP gas
¡¤ For use in single rod or dual rod/remote sense applications
¡¤ Includes spark cable adapters to allow field replacement of both Honeywell and competitive controls without replacing existing spark cable.
For a full list of all the models this replaces, please check the charts that are uploaded into the gallery to check if your model is listed, thanks!
LED Error Codes:
OFF: No call for heat, TH-W does not have 24VAC present
Fast Flash: Power up – internal check
Heart beat (1/2 sec bright, 1/2 dim cycles): Normal start up, ignition sequence started
4 secs on then x flashes: Device in run mode. “x” = flame current
2 flashes: 5 minute retry delay
3 flashes: Flame failed during run
4 flashes: Flame sensed out of sequence
5 flashes: Damper error. Make sure 24V terminal is not connected if P1 plug is not used
6 flashes: Control internal error
7 flashes: Flame rod shorted to ground
8 flashes: Low secondary voltage supply. Check transformer and AC line
TH-W should be connected to 24VAC from the thermostat
24V GND should be connected to the unswitched leg of 24VAC transformer
24V should NOT be connected if P1 vent damper is not used
DISCLAIMER: Failure to follow instructions carefully can result in injury or cause damage to the product. Check the ratings given in the instructions to make sure the S8610U module is suitable for your application. The installer must be a trained, experienced service technician. After installation is complete, check out operation as provided in these instructions. Babybluetriton is not responsible for how the product is installed.